for Springfield, OH
Good estimate, explained clearly.
Lynn - Springfield, OH
Tech asked and listened to my preferences. Took great care with shoe covers, and my pets. I’m completely pleased with my estimate.
Great service. Problem solving. Good experience.
Ralph - Springfield, OH
Very knowledgeable, friendly and pleasant
Tennis mom - Springfield, OH
Josh was very knowledgeable with all the options. He went through different options for me and explained each option. He asked a lot of questions to figure out which one would be the best option for me. He did all the figuring out part with me so it was easy for me to figure out which one would serve me the best!
Tharp - Springfield, OH
Josh was awesome! Will use again in future if I need to.
Thompson - Springfield, OH
Great information - answered all of my questions. After comparing Train, Lennox and Carrier for quality, efficiency, warranty, and cost I went with Carrier and Xenia Heating and Air.
Customer stated heat went out last night. Restarted system inducer would come on system would then flash pressure switch error. Checked all hoses and condensate drain for clogs found none. Removed pvc vent pipe as well found no issues with air flow. Tested pressure switch with dual port manometer and in doing so discovered the pressure switch wasn’t always opening or closing when it should be. Amp drawl on inducer motor would bounce back and forth between 068 and 073. Of a max 070. Contacted landlord and discussed options. Parts will be ordered for repair and i will return with portable heater for customer.Further advised landlord unknown if any further problems until pressure switch is replaced
Estimate for new furnace
Performed Our Professional Whole House Duct Cleaning Service
Dropped off motor for repair