Performed complete tuneup and safety inspection on a Williamson furnace; as well as, a thorough duct cleaning to ensure efficient
operation for the winter season of 2019/2020.
Tech went out to preform pre season gas furnace check out, customer was not home
Customer requested gas furnace tune up for fall 2019
Combed and straightened the coil fins on a Luxaire A/C Condenser.
Goodman AC repair
Replaced dual capacitor on Bryant ac unit
Upon inspection of an older Lennox AC system, found the outdoor unit coil dirty. Cleaned off coil and unit is operating within manufactures specifications.
Estimate provided to replace a 1992 Carrier AC with a Carrier 13 SEER 3 Ton Air Conditioner. Included a one year service maintenance agreement.